Moon Air provides fast, reliable air conditioning, heating, and electrical services to the residents of Claymont, DE and the surrounding areas!
We pride ourselves on a high standard of customer service. Read our reviews and find out why your neighbors consider us to be their preferred HVAC company and electrician in Claymont, DE.
for Claymont, DE
Our Reviews by City
Always a lovely visit
Ricketts - Claymont, DE
Craig is wonderful.. at this point he's a friend!
Great service, friendly,
Spiess - Claymont, DE
Excellent service, very informative!
Eric - Claymont, DE
Cooling Rejuvenation Outdoor unit voltage enhancement system read 5/42.6 with a factory setting of 5/45 and is below the allowable fault. Platinum repair done 8/23/2019 carries 2 years warranty. Performed warranty repair. System amps are within allowable ranges. FLA 0.7 with a factory setting of 1.5 and RLA 6.0 with a factory setting of 17.9. Informed customer if voltage enhancement system fails again recommend service tech look over system if thereâ€™s an underlying cause. Indoor unit supply 54 with a 70 return and 16 delta. Static pressure is fine. Voltage enhancement system read 20 with a factory setting of 20. Board and connections good. Filters a little dirty, recommend replacing end of September. Coil clean both sides as is pan. System normal operation at this time.
Cooling Rejuvenation Outdoor unit voltage enhancement system read 5/43.6 with a factory setting of 5/45. FLA 0.5 and RLA 6. Cleaned coil, interior and exterior. Checked disconnect and wiring connections for safety. Found loose conduit with burned portion of UF wire on ground. Showed customer, wire was disconnected from circuit. Indoor unit supply 47 with a 66 return and 19 delta. UV system has power, lamp no longer working at this time. Air ranger media recently replaced. Found bag of extra air rangers behind filter in return. Customer concerned with louder blower, sounds within normal operation. Blower amps 8.5. Blower spins without restriction. Coil and pan clean. System normal operation at this time.
Daikin 5 zone mini split system
Installing Daikin 5 zone mini split system
No A/C second floor apartment, checked system and found low voltage circuit protection system had failed due to shorted coil on the outdoor unit gateway, installed replacement circuit protection and gateway test ran.
A/C Rejuvenation Indoor: checked for any burnt or loose connections, blower is clean, cleaned out cabinet, capacitor still in factory spec, air ranger filter was changed at beginning of month. Outdoor: checked for any burnt or loose connections, found a few marks on the thermostat wire and it was showing bare wire so I put some electrical tape around those spot, capacitor was still in factory spec and coils were good, cleaned out electrical cabinet, and whipped down unit. Unit is ready for the summer
See previous invoice
Installed ez trap. Checked ac. Checked all eletrical connections test drain line with 1 gal of water. Cleaned outdoor coil checked voltage enhancement system. Checked fla and rla test ran ac operation normal at this time
Furnace rejuvenation checked inducer amps checked blower amps checked all electrical connections. Checked voltage enhancement system checked heat rise operation normal at this time
customer is signing up for the gold club plan and 3 mini split add ons
Club service gas heat, test ran system, inducer fan amps 1.2, glow bar .8, indoor fan 4.7, flame current 2.4uamps, air filter clean. Factory spec temp rise 30 to 60 degrees, actual 49 degrees, operation normal at this time.
Club service, Mini-Split System, two outdoor units and five head units, cleaned all air filters and checked for any fault codes, both systems are within factory spec at this time.
Customer brought a concern to my attention. The flames would come on but after the inducer motore would modulate for a couple minutes like someone is revenge an engine then eventually the whole system would come on. Checked system and found that the indoor control system is starting to fail, 10 year parts until March 23 2021, installed replacement control and also completed club service. Inducer fan amps 2.4, glow bar .6, indoor fan amps 4.1, flame current 1.4uamps, removed and cleaned sensor now at 2.8uamps, 40 degree temperature rise, filters need to be changed.
Delta t 45 Delta t 48 Air circulation system is clean
Delta t 44 Base .6 Ignitor .5 Air circulation 4.5 Sencer 5.7 Voltage enhancement system 20 Filter is clean but the wrong size The real size of the filter is 20x25x1 Air circulation system is dirty Everything beside the Air circulation system is in factory spects at this time
Indoor unit has a supply of 129 and a return of 84 with a 45 heat rise. Turned gas off at fuel delivery system and ignition ceases. Ignition occurred with no issues with flame ignition system. Flames are blue, straight and no flames are dancing or rolling back. System satisfied temperature on thermostat and cut gas off. Gas shut off on gas line working as intended. Exhaust removal amps read 0.9 with a factory setting of 1.05. Blower wheel clean, spins without restriction and the bearing is tight. Blower amps read 5.5. Voltage enhancement system read 19.5 with a factory setting of 20 and is within allowable fault. Static pressure supply read 0.18 and return read -0.08. System normal operation at this time.
Goodman 2.5 ton AC and Coil with new thermostat
Clean and checked a/c system, 21 degree temperature split across indoor coil, air filter had been changed recently but recommend replacing soon, blower wheel was clean and condensate removal system working properly. All voltages, amperages and systems were all within manufacturers specs for indoor and outdoor units, system is working normally at this time.
14 SEER 2 Ton AC and 80% 60k furnace
Club service gas with A/C, outdoor system was very dirty, chemically cleaned and test ran, 18 degrees delta t, compressor run load amps factory spec 15.4, 7.4, outdoor fan full load amps factory spec. 95, actual. 9, voltage enhancement system factory spec 45/5, actual 44.7/4.8, within factory specifications. Test ran furnace and changed customer supplied filter, inducer fan amps. 4, glow bar .3, flame current 2.2 uamps, indoor fan 2.6, operation normal at this time.
Installing 14 SEER 2 Ton AC and 80% 60k Furnace with new line set and thermostat. 10 year parts, 10 year compressor, lifetime heat exchanger, and 1 year labor warranty
Installing Goodman 14 SEER 2.5 Ton AC and coil with new line set and condensate pump to re-route the drain out by the condenser. We will also perform a â€œtune-upâ€ and check over of our furnace that we installed. Install scheduled for 9/28 when Justin is back in town
Ower stated water was entering inside panel from main cable. Removed meter cover and sealed load side cable with silicone caulk. Removed pvc lb cover and took picture of sediment lining in lb bottom. Seal back opening with duct seal to prevent any water from entering home .
Performed electrical inspection on basement outlets and switches. There are a few minor fixes to be done. Installed GFCI outlet BEHIND bar and tightened all outlets and put plates where necessary.
Club service A/C, changed customer supplied air filters, 2 - 16x25x1, test ran system in cooling, 18 degree delta t, compressor run load amps factory spec 17.9, actual 8.6, outdoor fan full load amps factory spec 1.5, actual 2.2 voltage enhancement system factory spec 45/5, actual 44.5/4.9, operation within factory specifications at this time.