Moon Air provides fast, reliable air conditioning, heating, and electrical services to the residents of Worton, MD and the surrounding areas!
We pride ourselves on a high standard of customer service. Read our reviews and find out why your neighbors consider us to be their preferred HVAC company and electrician in Worton, MD.
for Worton, MD
Our Reviews by City
Foreman - Worton, MD
It was a process. Just watching the technicians do a nonstop job was truly amazing.
Foreman - Worton, MD
Steve was very patient. And very knowledgeable about his job. An asset to moon air.
Shields - Worton, MD
Jenkins - Worton, MD
Justin and Omar were a great team. They worked efficiently with little disruption to our daily routine. Both Justin and Omar were very polite and friendly and Justin took the time to explain everything.
Shields - Worton, MD
Myers - Worton, MD
Craig did a great job! Very pleased w work done and politeness
Coleman - Worton, MD
Gary - Worton, MD
Joe explains what he is doing and why
The furnace supply reads 126 with a return of 71 making our heat rise 55. Voltage enhancement system reads 12.2 with a factory setting of 12.5 fan blower, burners, and flame sensor are in good condition. Also coils and Heat exchanger are In good condition. Furnace seems to be in good condition.
Bronze package 14 seer
Daikin 4-zone mini split with 7k, 9k, 9k, and 15k wall units
Outdoor unit crawl space 5/35. Fixed a wiring connection. Cleaned unit. Outdoor unit attic read 5/39.9. Checked wiring conecctions. Cleaned unit. Outdoor unit mini split coil cleaned and connections fine. Indoor unit crawl space 60 supply 76 return and 16 delta. Voltage enhancement system read 9.9 with a factory setting of 10. System normal operation at this time. Changed nozzle, strainer, gaskets and filter for oil boiler. Bled air out of system, test ran 10 minutes. System normal operation at this time.
See previous invoice
Oil/ac cleaning. Changed nozzle and filter Changd gaskets. Cleaned cad cell checked ignition transformer. Checked air filter it look fine. 17 degree split drain line is clear Outdoor coil is clean Voltage enhancement system read within factory spec voltage gateway is not pitted rla and fla within factory specs operation normal at this time
Installing Daikin 4-zone mini split with 7k, 9k, 9k, and 15k wall units Scheduled install for 9/21 and 9/22
Daikin single zone 19 SEER 24k mini split
Daikin single zone 19 SEER 24k mini split. This includes a $500 sponsorship from Moon Air which will provide 2-3 â€œdropsâ€ a day planned for right after the daily weather.
Cooling Rejuvenation x 2 Outdoor unit 1st floor voltage enhancement system read 5/39.8 with a factory setting of 5/40. FLA 1.1 actual 0.55 and RLA 12.8 actual 5.8. Cleaned coil and exterior, interior drain clear. Checked disconnect and wiring connections for safety. Outdoor unit 2nd floor voltage enhancement system read 5/35 with a factory setting of 5/35. FLA 0.6 actual 0.55 and RLA 4.5 actual 13.5. Cleaned coil and exterior, interior drain holes clear. Checked disconnect and wiring connections for safety. Indoor unit 1st floor has a supply of 57 with a 73 return and 16 delta. Static pressure is fine. Voltage enhancement system read 15 with a factory setting of 15. Coil clean both sides as is pan. Blower spins without restriction. Board normal operation at this time despite rough shape. Checked wiring connections. Changed air filter customer supplied. System normal operation at this time. Indoor unit attic has a supply of 76 with a 92 return and 16 delta. Static pressure is fine.
Daikin 4-zone mini split system
Daikin 4 zone mini split system with 18k wall unit for the living room, 12k for the master bedroom, and 7k for the smaller 2 bedrooms.
Installing Daikin 4 zone mini split system with 18k wall unit for the living room, 12k for the master bedroom, and 7k for the smaller 2 bedrooms.
A/C Rejuvenation Preformed Inspected indoor unit, Electrical components and safety controls are working properly, return grill and plenum are clean, filter was restricted, replaced with new clean one, evaporator coil is clean, blower is clean , supply and return is clean. Inspected all wiring for looseness, or burns. Inspected all electrical components for proper functionality and all components are within recommended range Ducts are properly installed and secure Inspected outdoor unit. Electrical Components are working properly, refrigerant pressures good. Cleaned cabinet and washed out coil. Inspected all wiring for looseness and burns. Inspected all electrical components for proper functionality and components are within recommended ranges Ordered replacement filters for homeowner Unit is properly cooling at this point in time
See previous invoice#,moon
Heating Rejuvenation x 3 Outdoor coil attic voltage enhancement system read 45.8uf with a factory setting of 45uf and is within allowable fault. The RLA was 6.4. Board and connections are good. Indoor unit has a 92 supply and 74 return. With auxiliary heat the supply went up to 119. Static pressure supply is 0.5 and return was 0. Blower amps were 1.8 and heat kit amps 19.5. Coil clean on both sides. Blower looks fine, cleaned one fin no difference. Blower spins without restriction and the bearing is tight. Changed three filters customer supplied in upstairs. Changed filter in hallway customer supplied. 1.8a, 19.5a Indoor unit living room 90 supply 73 return. Cleaned filter and exterior of system. Indoor unit dining room 91 supply and a 78 return. Cleaned filter and exterior of unit. System normal operation at this time. Indoor unit bedroom 87 supply and 67 return. Cleaned filter and exterior. System normal operation at this time. Indoor unit mothers room 90 supply and a 67 retu
Return vist installed heat atrip kit test ran operation normal at this time
Delta t 24 Voltage enhancement system 20 Air circulation system is clean Sensor was cleaned Base 2.8 Igniter .2 Sensor 6.2 Air circulation system 3.7 Everything is in factory spects at this time
Changed the oil filter Changed the nozzle The Sensor was checked Filter was cleaned The gun of the system was cleaned Air circulation was cleaned Replace the 6in smoke pipe Checked the chimney Voltage enhancement system 7.4 Everything is in factory spects at this time
Indoor unit has a supply of 121 with a 72 return and 49 heat rise. Exhaust removal amps read 0.38 with an FLA of 0.38. Static pressure supply read 0.6 and return -0.3. Gas shut off works on both fuel delivery system and gas line. Voltage enhancement system read 5 with a factory setting of 5 on exhaust removal system. The voltage enhancement system read 15 with a factory setting of 15. Blower wheel clean, spins without restriction and the bearing is tight. Cleaned flame safety system and burners. Cleaner out rust out of ignition box. Ignition occurred no problem, flames blue and straight. Blower amps read 4.8. Checked heat exchanger for safety, and checked filter. System normal operation at this time.
Upon arrvial found dran line clogged and and vinyl tubing partially kinked fixed tubing and vacuumed out drain line tested with two gallons of water also found that the living room unit needs to be remounted (see photo).
Did check on airconditioning system checked parts and operations, system is working normally at this time.
Did clean and check on air conditioning system, checked parts and operations, checked temperature split across the indoor coil, checked voltage enhancement systems. System is working normally at this time.
Installing 2 ton 3 zone system with 12 year parts and labor
Indoor unit had a supply of 63 and a return of 76 with a 13 delta. Suction line is cold and liquid line warm. Voltage enhancement system read 7.4 with a factory setting of 7.5 and is within allowable fault. Cleaned coil, black dots didnâ€™t come off. Cleaned pan and drain line with cleaner. Secured insulation to inside door to coil and sealed bottom so air wonâ€™t escape. Checked filter and is clean. Outdoor unit voltage enhancement system read 4.9/40 with a factory setting of 5/40 and is within allowable fault. Cleaned coil and exterior, interior drain holes clear. Checked disconnect for safety and system normal operation at this time. During maintenance noticed main wire going into meter box outside has exposed neutral wires and sleeve has fallen off along the wire. Recommend electrician come out and give quote.