Moon Air provides fast, reliable air conditioning, heating, and electrical services to the residents of Middletown, DE and the surrounding areas!
We pride ourselves on a high standard of customer service. Read our reviews and find out why your neighbors consider us to be their preferred HVAC company and electrician in Middletown, DE.
for Middletown, DE
Our Reviews by City
Greene - Middletown, DE
Thank God for them. There is alot taken for granted when anyone ever has to live without heat in the winter. I always felt for them but never had to experience what it really felt like. Now I know. Looking forward to having Moon taking good care of the units in my house. Thank you for your kind service.
Lemon - Middletown, DE
It appears he did very well. I will have my husband check it when he gets home. Greg was very professional and informative. Thank you for the service
Professional, courteous service
Delbueno - Middletown, DE
Craig was friendly, courteous, knowledgeable, and professional
Pooley - Middletown, DE
Very nice and explained everything that was going on.
Roth - Middletown, DE
Good service and price. Prompt and skilled professional.
Watson - Middletown, DE
Watson - Middletown, DE
Clay & Greg did a very thorough diagnosis of my AC system and explained their findings clearly. I appreciated their honest opinions on the issues and options.
Great service , not happy about having to replace the thermostat after 5 years though
Kruesi - Middletown, DE
Techs were friendly and professional and quick
Watson - Middletown, DE
Very thorough and The service technician explained everything he was doing very clearly.
Schroeder - Middletown, DE
Service man was on time, thorough, and polite
Very good service
Watson - Middletown, DE
Tankless Water Heater
Carla - Middletown, DE
After 3 other companies could not help me Clay arrived and completed the work efficiently and timely. Thank you
Great Service folks, but very poor business practice
Dushyant - Middletown, DE
All of the people I dealt with are Awesome folks, but I think they have been provided not so good business practice workflow.. I understand that every opportunity the vendor gets it's a potential lead for more business.. But looks like management lacks understanding on how to put Customer experience first. To summarize, with each visit the amount of recommended service goes up with greater amount spending.. I get that, the proactive corrective action can prevent costly repair later.. But when the customer calls to get a issue fix, they just the issue fixed and not be told for many other issues that might come.. I just felt like you guys just wanted to get more and more money.. Sorry.
Quick and Efficient
Mark - Middletown, DE
Great service. Was even early and explained everything
Roberta - Middletown, DE
Lisa - Middletown, DE
It was very fast. I called this morning because our AC would not come on yesterday and a technician came out the same day. Very fast and excellent service. Thank you.
William - Middletown, DE
Technician was very pleasant & knowledgeable & performed work in a very professionable mannner .
Great service & very informative!
Chris - Middletown, DE
Clay was very informative by taking the time to explaine & show everything he was talking about was wrong with our heater to me. He then explained same thing to my husband over the phone, as he was unable to be there. His service was outstanding!!
Garrett - Middletown, DE
lisa - Middletown, DE
Checked outlets in kitchen,found a defective GFCI outlet . Customer chose the band aid repair.
Indoor unit has a supply of 56 and a return of 69 with a 13 delta. Voltage enhancement system read 12.3 with a factory setting of 12.5 and is within allowable fault. Blower wheel is clean still and spins without restriction. Board and connections are good. Replaced filter customer supplied she has 1 left. Pan is clean and replaced pan treatment. Inside of coil dirty, cleaned both sides. Outdoor unit voltage enhancement system read 5/34.1 with a factory setting of 5/35 and is within allowable fault. The FLA is 0.6 with a factory setting of 0.7 and the RLA is 4.4 with a factory setting of 13.5. Coil dirty due to grass being cut, cleaned coil and exterior. Interior clear and checked disconnect for safety. System normal operation at this time.
No A/C, system not running, checked and found service switch off for the furnace, put toon and test ran, suction 74, liquid 200, unit is 17 years old and do not recommend any repairs at this time, supply air 57 degree return 80 for a delta t of 23 degrees.
Return temperature 68. degrees. Supply temperature 50 degrees total delta t 18 degreesfilter looks ok, recommend changing filter in a couple of months. Blower wheel is clean and did not see or feel any oil on or around hub and motor, blower motor amps 10.8 on high speed, Blower voltage enhancement system read 10.5 uf vs factory spec of 10 uf. Evaporator is clean and did not see any oil spots, checked condensate drain and it does have some slight build up recommend and ez trap to shut system if a clog does developed in the future. Checked outdoor system coil was a little dirty used water to rinse off coil. Rla 7.5, fla 0.9, voltage enhacement system read 44.1/4.8 which is within allowable fault. Voltage gateway had some pitting suction line sweaty and liquid line warming up operation normal at this time.
Club service A/C two systems, both had new air filters installed, test ran both systems, 2nd floor system 18 degree delta t, 1st floor system 19 degree delta t. Outdoor Unit serial number 4507E05684, compressor run load amps factory spec, 14.4 actual, 7.6, outdoor fan full load amps factory spec, 1.1 actual, 1.0, voltage enhancement system factory spec 50/5, actual 48.9/4.9. Serial Number 2807E15609, compressor run load amps factory spec, 19.2, actual 9.9, outdoor fan full load amps factory spec, 1.4, actual 1.1, voltage enhancement system factory spec, 60/5, actual 61.7/4.9, operation within factory specifications at this time. Installed condensate removal system for the 1st floor system, checked with water and cleared the discharge line with CO2.
Club ac service. Return temperature 69 degrees, supply temperature 51 degrees total delta t of 18 degrees. Changed very dirty air ranger filter with new one provided by customer he has one more left. Cleaned ez trap tubing and saftey sensor. cleared drain with galo gun and descaler did not detect any clogs. Checked blower motor amps which are between 2.9-3.1, and the wheel is clean. Checked Evaporator coil which is clean and pan as well, took out old pan treatment and replaced with new one. Changed humidifier from winter mode to summer mode. Checked outdoor system. Coil is clean and drain holes are as well. Checked voltage gateway which haves no pitting and getting proper voltage 244 volts in and out. Checked voltage enhancement system and it read 46.4/4.9 vs factory spec of 45/5 which, ears it's within allowable fault. Brushed out electrical compartment, checked all electrical connections rla read 9.8 vs factory spec of 28.6. Fla read 0.3 vs factory spec of 1.
Leak from water heater check and found cold water bypass to mixing valve had failed installed replacement check for leaks okay at this time.
Installing Platinum HVAC package for main house (including humidifier, return drop ductwork, duct cleaning, and Honeywell T10 thermostat) and a single zone mini split for the bonus room upstairs.
Returned and installed replacement fuel delivery systemm, removed and cleaned burners and flame sensor, test ran equipment, operation normal at this time.
Club serivce follow up, furnace does not heat sometimes, cycled system and found very low flame current, less than 1 uamp, removed and cleaned sensor now at 2.2 uamps, no other problems found, installed replacement proving system and test ran, operation normal at this time.
b Service. Successfully ran gas warm air furnace through all stages of operation. Return temperature 75 degrees, warm supply temperature 130 degrees, total heat rise 35 degrees. Changed filter provided by customer. Draft motor amps were 1.20 vs factory spec of 1.33 which means it is within allowable fault.Within a timely manner the gas ignited into a solid blue flame with no yellow tips. Cleaned flame sensor, burners look new and in good condition. Innspected blower motor wheel which looks dirty and recommend cleaning. Blower motor amps were 4.5. tightened all screws, and electrical connections. Furnace is in proper working order at this time.
club oil service. changed filter, cleaned oil canister, changed all gaskets, oil strainer looks clear, changed nozzle 1.25, 80a. cleaned electrodes, adjusted electrodes, cleaned gun with wire brush, smoke test came up clear vamcummed heat exchanger. homeowner is low on oil recommed getting oil.
Reconnected wiring in panel
Reconnected wiring in panel
Reconnected wiring in panel
Indoor unit in heating has a supply of 135 with a 76 return and a 59 delta. Both humidifier filter and air filter look fine, recommend checking air filter at end of December. Voltage enhancement system read 10 with a factory setting of 10 on blower assembly. Board has no burn marks on it and connections are tight. Blower wheel and compartment look good, blower wheel spins without restriction and the bearing is tight. Exhaust removal system voltage enhancement system read 5 with a factory setting of 5. Exhaust removal system spins without restriction or sound. Cleaned the flame safety system and the burners, both look good. Ignitor looks fine, ignited gas no problems. Ignition occurred with no problems, flame was blue with no flames rolling back. Blower amps were 7.6, ignitor amps were 0.5, high limit amps were 0.4 and pressure switch amps were 0.4. Indoor coil and pan look good, installed pan treatment. Unit normal operation at this time and wiped down exterior of unit, recommend air c
Club Service. Successfully ran three year old lp gas warm air furnace through operation. did combustion test 02 7.4%, co2 8.9%, 92% ef, 50% ea, stack temp 100.4 degrees. theromostat sasified at 70 degrees to 72 less then 30 mins. Return temperature 70 degrees, warm supply temperature 105 degrees, total heat rise 35 degrees. filter looks clean and recently changed by customer. igniter read 55 ohms at room temp. Draft motor amps were 2.8. Within a timely manner the gas ignited into a solid blue flame with no yellow tips or roll backs. adjusted gas manifold pressure from 10 w.c to 9.7 w.c. Cleaned flame sensor, cleaned all burners, brushed off control board, cleaned inside and outside cabinet with microfiber towel, and vacuumed throughout. Inspected blower motor wheel which looks clean and runs without restriction. Blower motor amps were 3.8. and its voltage enhancement system read 12.1 vs factory spec of 12. which means it is also within allowable fault. Tightened all screws, and e
No AC call. Upon arrival customer informed that the air just didn't seem cool. Checked the air filtration system and it was clean. Checked evaporator coil system and it was clean. Went to the condenser outside to look at it. Condenser coil was dirty and needed cleaning. Opened voltage compartment and found d many faults with the voltage enhancement system. Spoke with customer and he also agreed. Replaced voltage enhancement system, gateway and added pumping system starter. Cleaned condenser coil system. Repaired and replaced all necessary wires and connections. Started unit up. Air removal and pumping system running proper voltage and amperes. Delta T at 20 degrees.
Furnace rejuvenation lp. Replaced air filtration system per customer. Last replacement was in April of this year. Air movement and circulation system clean. Water removal system clear. Cleaned sensor system. Ignition system has no cracks or hot spots. Cleaned flame distribution system. Air movement capacitance fully charged. Flame rectification proven. All systems running at proper voltage and amperes. Fuel distribution system set at proper pressure. All safety systems working properly. Temperature rise within factory specifications. No other concerns at this time.
Need estimate to replace gas lines to furnace, water heater and stove.
In heating the supply is 121 and a 74 return with a 47 delta. Blower wheel was a little dirty, compartment look good. Cleaned blower wheel and it spins without restriction and the bearing is tight. Inducer spins without restriction and both condensate lines for the primary and secondary heat exchangers look good. Changed humidifier filter customer supplied and cleaned humidifier and cleared it's condensate line with c02 onto a paper towel. Evaporator coil looks good. Cleaned burners and the flame sensor, burners look good with no distortions on the fins. The ignitor has a white mark on it, but was able to ignite with no problems. Ignition occurred with no problems, flames were blue with hints of orange and no flames rolling back. Inducer amps were 0.5 and the blower amps were 2.4. Cleaned indoor unit.
Provided quote for full basement remodel
Install follow up, customer stated that the indoor fan for the basement system the fan was not running on fan on at the stat, checked system and found that the inddor air movement system was running, set at 25% for fan only, changed to 55% per customer request.
In heat the supply is 120 and the return is 76 with a 44 delta. Blower wheel spins without restriction and the bearing is tight. Voltage absorption system read 19.8 with a factory setting of 20. Inducer motor spins without restriction. The condensate line from secondary heat exchanger is clear. Cleaned flame sensor, flame ignitor looks good. Burners look good with no warping or obstruction on fins. Inducer motor amps were 2.2 and blower motor amps were 4.7. Ignition occurred no problems, flame was blue with hints of orange and had good shape. In coiling the supply was 56 with a 73 return and a 17 delta. Air filter was checked and looks ok, recommend checking at end of the month. Cleaned exterior of furnace.
Replaced regulator and all gas line to furnace, stove and water heater.