Moon Air provides fast, reliable air conditioning, heating, and electrical services to the residents of Hockessin, DE and the surrounding areas!
We pride ourselves on a high standard of customer service. Read our reviews and find out why your neighbors consider us to be their preferred HVAC company and electrician in Hockessin, DE.
for Hockessin, DE
Our Reviews by City
Gillin - Hockessin, DE
03 - Hockessin, DE
Estimator was on time and detailed everything, installers were on time and removed the old unit installed the new as smooth as can be. Very nice Job.. I will share this with my family ,friends and business associates. j.
Great service, timely, and fair price
Roop - Hockessin, DE
John - Hockessin, DE
Had great service as usual from Moon
Very happy with the service received - my heater was fixed and working I no time at all great service - price wasn't too bad either
Joanie - Hockessin, DE
Would recommend Moon air to others
Prompt,thorough and friendly. Awesome prices.
Steven - Hockessin, DE
New circuit install
John - Hockessin, DE
Went over wiring and made necessary corrections so that the system would operate as duel fuel. Started and tested equipment, system is working normally at this time.
Replaced 1 wired and 4 wireless controllers. Need to try external mounted condensate pump.
Attic 80% 80k furnace and 3 ton AC
Getting a 20 degree delta t. Filter is clean. Tighten all screws and eletrical connections. Checked blower, evaporator coil, and pan all are clean checked duct work and it is clear of debris. Checked drain line and did not detect any clogs. Checked outdoor system. Cleaned outdoor coil. Checked voltage gateway and it has no pitting. Checked voltage enhancement system and it read within factory specs. Rla read 5.7, fla read 0.9. Brushed out eletrical cabinet. Operation normal at this time
Replace main control board in roof top unit, system that is on the right side of restaurant if you walk in front door. Started and tested equipment, system is working at this time. Recommend servicing entire system and do a good cleaning. Blower wheel is caked up with grease and dirt very badly. Left for the day will send check in.
Found circuit board in package unit failed, it has 24volts to the tstat and up to control board but no voltage from y terminal out to contactor, circuit board needs to be replaced.
Supply air temperature is 55 and return air temperature is 72 with a 17 delta. Static pressure supply is .5 and the return is -0.01. Replaced the air filter customer supplied. Blower wheel is dirty and bearing wheel is good. Voltage enhancement system read 15 with a factory setting of 15. In heat mode supply is 146 and return is 81 and a 65 heat rise. Exhaust removal system amps read 1.5 with a factory setting of 2.8 and are good. Tested gas shutoff and worked. System restored to normal and removing exhaust perfectly. Outside coil voltage enhancement system read 4.9 and 46 with a factory setting of 45 and is within allowable fault. Coil looks fine though a litt.e dirty. Checked disconnect for safety and system normal operation at this time.
Daikin 17 SEER 12k mini split with 10 year parts and 12 year
Installing Single Zone Daikin 17 SEER 12k BTU Mini Split System with 10 year parts and 12 year labor warranty Indoor wall unit to be installed centered between the front wall and the bulk head. The space is 82.5â€ wide and the indoor unit is 35â€ wide. The line set should come out underneath the chimney in the opening between the two supports (see pictures). Chris will drill a pilot hole and prep before we get there to make sure that there are no wires in the way. Based on my measurements the line set should come out 50â€+ from the front wall and the edge of that foundation is 48â€ so we should be good to take our lines straight out from the back of the unit. No line hide will be needed because of the short run to the outdoor unit. Just need to be conscious of the minimum line set length.
Found contactor for 1st floor system failed, replaced it with new, system is now working normally at this time.
checked operations of heater and checked operation of A/C unit. Both operating within factory specs.
Two Daikin 5 zone systems
Outdoor unit voltage enhancement system read 5/44.4 and is within allowable fault. The FLA is 0.6 with a factory setting of 0.95 and the RLA is 6.8 with a factory setting of 17.9 both good readings. Cleaned coil and cleaned out interior of debris. Checked disconnect and connections are snug. Indoor unit has a supply of 43 and a return of 65 with a 22 delta. Changed air filter customer supplied they have 3 left. Checked electrical connections on board and they look good. Cleaned condensate line. Pan and coil both look great recommend a pan treatment to keep pan clean and condensate line clear. Blower wheel is clean and spins without restriction with a tight bearing and amp reading of 1.9. System normal operation at this time.
Club service A/C, checked system operation, 18 degrees delta t, checked all electrical connections, indoor coil and blower wheel clean, test ran in both heat and cool, operation normal at this time.
Installing two Daikin 5 zone systems with wall mounts, DZK kits and FDMQ ceiling mounts to condition your 5,000 square foot barn renovation. All equipment is covered by a 12 year parts and 12 year labor warranty
92% furnace and 14 SEER AC
Help install with flue liner.
Installing 92% furnace and 14 SEER AC with new chimney liner, thermostat, and 10 year parts / 10 year labor warranty
Club service gas warm air, checked operation in both high and low fire, manifold pressure in low1.7"wc, high 3.4"wc, inducer fan amps .4, glow bar .6, indoor fan 1.9, checked EAC cells and per-filters, clean, test ran bypass humidifier and opened damper.
No heat new install, checked system and found that the electronic gas control was turned off, reset and test ran unit, also checked indoor air filter, operation normal at this time.
Outdoor system for 2nd floor not running. Checked voltage and had power. Checked voltage enhancement system and found it had lost its capacitance. Replaced and system is running now.
14 SEER 3.5 Ton Furnace and 92% 100k BTU Furnace
16 SEER 2-Stage AC, help with install, wired in low voltage and sim module.
Installing Amana 14 SEER 3.5 Ton AC and 92% 100k BTU Furnace
Installing new Amana 16 SEER 2-Stage 4 Ton AC with 10 year parts, 10 year labor and lifetime unit replacement warranty