Moon Air provides fast, reliable air conditioning, heating, and electrical services to the residents of Galena, MD and the surrounding areas!
We pride ourselves on a high standard of customer service. Read our reviews and find out why your neighbors consider us to be their preferred HVAC company and electrician in Galena, MD.
for Galena, MD
Our Reviews by City
Duke - Galena, MD
Greg was prompt, courteous, and professional.
Larry M - Galena, MD
Justin and Omar worked diligently to install our new HVAC system in one day. All work was neat and thorough. Very professional.
Above and Beyond Service
CAS - Galena, MD
Clay found that the replacement part was damaged and went above and beyond to have another unit brought to him as he and his partner continued to work. The new unit was slightly larger so he had to make modifications for it. He is obviously very knowledgeable and customer oriented.
They were fantastic
Berger - Galena, MD
Very helpful, eased my mind
Bansbach - Galena, MD
It is refreshing to deal with a service company that keeps you updated on what is going on and does what they say they are going to do when they say they will do it.
Very good , experience
patrick - Galena, MD
Diane - Galena, MD
Thank you, awesome service!!
Diana - Galena, MD
Angela - Galena, MD
Returned an installed combustion blower test ran operation normal at this time
Upon arrival found service off at furnace. Turned switch back on and tested system in heating and cooling did furnace inspection. Filter is clean. Return temp 70 degrees supply temp 115, 45 degree heat rise. Flame sensor and burners are clean draft motor amps and blower amps within factory spec. Eletrical connections are tight. Heat exchanger has no areas of concern. Operation normal at this time
Furnace rejuv changed filter supplied by customer. Draft motor amps wit factory spec. Checked eletrical conections. Blower is clean getting 56 degree heat rise. Burners and flame sensor are clean checked heat exchanger and found no areas of concern. installed surge protector system operation normal at this time
Replace gas control and fixed leak next to shut off operation normal at this time.
See previous invoice
Cooling Rejuvenation Voltage enhancement system read 4.8/37.8 with a factory setting of 5/40 and is below the allowable fault. FLA 1.1 actual 0.55 and RLA 12.8 actual 4.8. Performed basic level warranty repair. Cleaned coil, interior and exterior. Checked disconnect and wiring connections for safety. Patched exposed lineset with insulated tape. New FLA 0.6 and new RLA 5.2. New voltage enhancement system read 5/40. Indoor unit supply 59 with a 76 return and 17 delta. Static pressure is fine. UV light working at this time. Turned water on to humidifier at customer request, might be something wrong with humidifier. Blower clean, spins without restriction. Board and connections are fine. Coil and pan good. System normal operation at this time.
Removed panel cover and found white wire lose. Tightened wire .
Cooling Rejuvenation Outdoor unit voltage enhancement system read 4.9/43.2 with a factory setting of 5/45. FLA 1.1 actual 0.6 and RLA 14.1 actual 5.8. Cleaned electrical compartment. Cleaned coil, interior and exterior. Checked wiring connections and disconnect for safety. Indoor unit supply 60 with a 78 return. Found return flex not secured to return box. Secured flex to box. Voltage enhancement system read 19.1 with a factory setting of 20. Sealed up parts of ductwork with tape. Cleaned EZ trap with brush. Coil is fine as is pan. System normal operation at this time.
renewing gold club plan with amanda
Checked pwerat panel, found neutral wire hooked up in wrong splice. Rewired and installed floods, everything working correctly.
Outdoor unit voltage enhancement system read 5/45 with a factory setting of 5/45. FLA 0.55 and RLA 6.0. Cleaned coil and exterior, interior clean. Checked disconnect for safety. Indoor unit supply 54 with a 74 return and 20 delta. Static pressure is fine. Coil and pan good. Cleaned drain line with brush. Changed air filter customer supplied. Blower clean, spins without restriction. Board and connections are fine. System normal operation at this time. Removed dead rodent from crawl space.
No A/C, checked system and found that the voltage enhancement system had failed, factory spec, 45/5, actual 0/0, installed replacement a d test ran, start up amps 23.4, installed compressor saver and dropped start to under 13 amps, operation normal at this time.
Daikin 3-zone mini split with 9k, 9k, and 18k indoor wall units
Daikin 4 zone mini split with 4 12k wall units
Installing Daikin 3-zone mini split with 9k, 9k, and 18k indoor wall units.
Electric water heater moved upstairs to laundry room
96% 80k lp furnace and 14 SEER 2.5 Ton AC
Installing Rheem 50 gal water heater with material and labor to move it upstairs to the laundry room.
Installing 96% 80k lp furnace and 14 SEER 2.5 Ton AC with new return drop and Oil tank removal from basement
Upon arrival found system going off on high limit changed fan speed checked air filter it is clean. Operation normal at this time
Club service, changed customer supplied air filter, inducer fan amps 3.0, glow bar .3, indoor fan 2.3, flame current 1.7uamps, remove and cleaned sensor now at 2.4uamps, main burners were very rusted, installed replacements.
Delta t 110 68 Base 2 Igniter 1.2 Air circulation system. 1.5 Sensor 8.4 Voltage enhancement system 4.9 Air circulation system is clean Filter was changed Everything is in factory spects at this time
Checked all eletrical connections, getting a 50 degree heat rise. Checked tubing, and tighten all screws. Did wd40 wipe down checked air filter it is clean. Cleaned burners, and flame sensor. Checked blower it is clean. draft motor amps 0.2. Blower motor amps 4.1. Operation normal at this time
Delta t 60 Amps 21.8 Air circulation was clean System was wiped down indide and out Everything is in factory spects
did furnace cleaning and complete heating system restoration.