Moon Air provides fast, reliable air conditioning, heating, and electrical services to the residents of Elkton, MD and the surrounding areas!
We pride ourselves on a high standard of customer service. Read our reviews and find out why your neighbors consider us to be their preferred HVAC company and electrican in Elkton, MD.
for Elkton, MD
Our Reviews by City
Shortall - Elkton, MD
Great service. I wouldn’t choose any other company
Ellis - Elkton, MD
Harman - Elkton, MD
Greg H was at my hone at 9:30 pm to fix my a c on the hottest day. He arrived at 9:30 pm and fixed our a c. And Tammy was so nice and worked with us to get Greg to our house!!!
Sclavos - Elkton, MD
Sclavos - Elkton, MD
Sclavos - Elkton, MD
Very courteous and professional!
Bristow - Elkton, MD
Combs - Elkton, MD
#JobWellDone Craig did an awesome job. Communication every step of the way!
Jeff - Elkton, MD
Clay and his assistant are amazing. They quickly fixed the issue and got our AC running again. Thank you so very much. We will be customers for life.
Great service !
Lyons - Elkton, MD
Quick service , professional and knowledgeable about the unit . Explained the problem and it was cooling quickly!!!
Bernardo - Elkton, MD
service Tech adjusted my fan speed. all good
marvel - Elkton, MD
My technician came in an emergency situation on the hottest day of the year. His name was Greg and he was very knowledgeable and fixed my unit in an hour and a half. HE was very professional and I had a great experience.
Very polite. Explained everything.
Hutchins - Elkton, MD
My first experience with Moon Air. I will highly recommend Moon Air to friends and family.
Zebley - Elkton, MD
Kocher - Elkton, MD
Air conditioner now set for season and soft stsrt added to compressor. Great service.
Tingley - Elkton, MD
Castro - Elkton, MD
Very good experience job done well
Quick response on a HOT summer day
Stephanie - Elkton, MD
Highly recommend Moon for repairs. Clay had our A/C back up in no time. Very polite and courteous staff in the office as well. Very impressed!
Great service all around!
Warhola - Elkton, MD
Clay was great! Very professional.
Angie - Elkton, MD
We placed an emergency repair call on a Sunday morning. The technician called us back right away and was immediately available to service our unit.
Farrell - Elkton, MD
Very prompt. Very courteous. Got a call beforehand saying he would here shortly & was. Explained the problem. Advised may need a new system soon.
Long - Elkton, MD
Irwin - Elkton, MD
Great service! The team was personal and professional. I would highly recommend them.
Awesome company to work with!
Vitak - Elkton, MD
Paul was Fantastic! My basement is a mess, filled with so many boxes and things so he had to work in extremely limited space. He handled it like a true pro and said he didn’t mind at all. Found the problem and fixed it immediately. Thank you Paul and Moon Services for always being professional, courteous and efficient.....Including Amanda who is always so upbeat and friendly on the phone.
Great Service, Great Techs
Karla - Elkton, MD
Justin and Jamir did an excellent job installing my system! They cleaned the basement floor before they brought anything in to protect the inside of my new furnace, placed protective covers over my floors, and wore shoe covers and masks in my house. The new AC unit went on a new plastic base and looks great. Justin gave me a rundown on the components of the new system so I have a better understanding of how it works; he is extremely knowledgeable and good at explaining in layman’s terms how it works. Excellent service overall!
Found thermocouple had failed, replaced with new, system is now working normally at this time.
Water leak from boiler, checked system and found that the expansion system has rotted and is leaking, drain the system and installed replacement expansion system and air removal system, refill and test for leaks.
Got system to run upon arrival however diagnostic LED is indicating a weak flame signal. Should be replaced as soon as possible so it's installed before it gets really cold
Flame sensor 4.9 au Base1.15amps Spark igniter works Indoor blower 1.45amps Unit in manufactur spect
Did clean and check on gas furnace, changed closet door filter and cleaned furnace filter, checked amperage of blower 7.2 amps, inducer 1.8 amps both within range, cleaned flame sensor, checked ignition system, gas pressure 9.8 in w.c. of 10 in w.c. per manufacturer, checked temp rise 40Â°F split and within manufacturers specs 25Â° to 55 Â° blower wheel and housing were clean and blower voltage enhancement system was within manufacturers specs, drain line free of debris and draining properly. Vacuumed out system and burners and wiped system with disinfecting spray. System in good working condition at this time.
Came out and gave quote for interlock kit. Costumer wants Roger filters.