Moon Air provides fast, reliable air conditioning, heating, and electrical services to the residents of Chadds Ford, PA and the surrounding areas!
We pride ourselves on a high standard of customer service. Read our reviews and find out why your neighbors consider us to be their preferred HVAC company and electrican in Chadds Ford, PA.
for Chadds Ford, PA
Our Reviews by City
Cooling Rejuvenation Outdoor unit voltage enhancement system read 5/43.7mfd with a factory setting of 5/45mfd and is within allowable fault. The FLA 0.6 and the RLA is 6.1. Cleaned outdoor coil and exterior, interior clear. Checked disconnect for safety. Indoor unit has a supply of 57 with a 75 return and 18 delta. Blower amps 4.9 and the voltage enhancement system read 9.9mfd with a factory setting of 10mfd and is within allowable fault. Board and connections good. Blower looks fine, spins without restriction. Indoor coil looks ok, as does pan. System normal operation at this time.
80% 60k furnace and 14 SEER 2 ton AC
Performed Ac tune up on Trane System also replaced hot water tank with 75 gallon tank, cycled systems all is working upon completion.
Replaced leaking evaporator coil on upstairs 2.5 ton Amana heat pump system that we installed 7 years ago. Replaced coil under Amana's 10 year all parts warranty. Customer received an upgraded all aluminum coil.