Moon Air provides fast, reliable air conditioning, heating, and electrical services to the residents of Bel Air, MD and the surrounding areas!
We pride ourselves on a high standard of customer service. Read our reviews and find out why your neighbors consider us to be their preferred HVAC company and electrican in Bel Air, MD.
for Bel Air, MD
Our Reviews by City
Quality service, dependable
Mount - Bel Air, MD
Moon always keeps us updated with maintenance service visits. Service personnel are very professional and explain what they did to service the equipment.
Very courteous and professional
Portell - Bel Air, MD
Steve - Bel Air, MD
Craig arrived and replaced our failed air condition at one of our remote equipment sites quickly and efficiently. We were able to get our space cooled quickly, which helped to prevent our equipment from overheating.
A/C Rejuvenation Preformed Inspected indoor unit, Electrical components and safety controls are working properly, return grill and plenum are clean, filters clean, evaporator coil is clean, blower is clean , supply and return is clean, blew out the condensation line. Ducts are properly installed and secure Inspected outdoor unit, checked for any burnt or loose connections, tested rating on capacitor, still in factory spec, refrigerant pressures good. Cleaned cabinet and inside and coils were clean. Unit is properly cooling at this point in time & ready for the summer.
Two System A/C Rejuvenation Preformed Inspected indoor units, Electrical components and safety controls are working properly, return grill and plenum are clean, filters replaced & clean, evaporator coil is clean, blower is clean , supply and return is clean Ducts are properly installed and secure Inspected outdoor units. Electrical Components are working properly, refrigerant pressures good. Cleaned cabinet. Cool is clean. Unit is properly cooling at this point in time
Single zone mini split for sunroom
Indoor unit attic has a supply of 136 with a 71 return and 65 heat rise. Static pressure supply is -0.2 and return is -0.4. Amp reading on exhaust removal system is 0.7. Voltage enhancement system read 7.5 with a factory setting of 7.5. Cleaned blower and flame sensing system. Burners look good as does ignition system. Board and connections good. Tested gas shut off on fuel delivery system and gas line. Checked heat exchanger for safety. Replaced filter customer supplied. Cleaned exterior of unit. Indoor unit basement has a 89 supply and 70 return. Static pressure supply is 0 and return is -0.4. Voltage enhancement system for exhaust removal system is 4.9uf with a factory setting of 5uf and is within allowable fault. Cleaned blower and flame sensing system. Changed air filter customer supplied. Board and connections are good. Tested gas shut off on fuel delivery system and gas line. Checked heat exchanger for safety. Cleaned exterior of unit. System normal operation at this time.
Cleaned and checked gas furnace, air filter was just changed, temp rise was 44Â° factory spec 45-65Â°, checked and cleaned flame sensor, blower wheel and housing were clean, checked ignition system, vacuumed out unit. System is working normally at this time.
Installed new cooling compressor for box.
Indoor unit has a supply of 52 with a 68 return and a 16 delta. Static pressure supply is 0.28 and return is -0.21. Blower wheel looks good, spins without restriction and the bearing is tight. Coil and pan both look fine. Cleaned air cleaner grate, filters are fine. Cleaned EZ trap with brush. Outdoor unit voltage enhancement system read 9.8/43.75 with a factory setting of 10/45 and is within allowable fault. The FLA is 1.1 with a factory setting of 1.7 and the RLA is 5.9 with a factory setting of 17.9. Inside of unit and coil is clean. Cleaned exterior and checked disconnect for safety. System normal operation at this time.
Lennox 14 SEER 3.5 Ton AC and 96% 110k BTU Furnace with 600M Bypass Humidifier
Installing new Lennox 14 SEER 3.5 Ton AC and 96% 110k BTU Furnace with 600M Bypass Humidifier
Callback - failed HVAC inspection Provided code compliant strapping of SEU cable and LT conduit Provided oxide inhibitor compound at aluminum line side connections Installed 20a2p circuit breaker Installed uv/mechanical protection at exposed exterior lineset.
Water leak at furnace, repaired and test ran #mmo
Replace the thermal system with climatemaster geothermal system
Central heating and air condition system installation
24-hour emergency service for oil-fired boiler
Installing a tankless water heater Navien
Tune ups on gas furnaces and air conditioners.
Working on a day and night air conditioner. Found the dual capacitor blown, replaced with American made part started and tested air conditioner- no other issues noted at this time, a new capacitor comes with a 5 year manufacturer's warranty.
Giving a free estiment on a gas furnace and air conditioning system. Client is talking about a Hybrid system