Moon Air provides fast, reliable air conditioning, heating, and electrical services to the residents of Bear, DE and the surrounding areas!
We pride ourselves on a high standard of customer service. Read our reviews and find out why your neighbors consider us to be their preferred HVAC company and electrician in Bear, DE.
for Bear, DE
Our Reviews by City
Jan - Bear, DE
I have always been pleased with Moon Services. Thank you
Ottolini - Bear, DE
what I wrote above says it all. They provide great service with a smile.
Very efficient serbice
Kucharski - Bear, DE
Routine Heating Tune up
Keith Davis - Bear, DE
Village - Bear, DE
Ottolini - Bear, DE
Greg did a fine job. He was quick and efficient.
Mauro - Bear, DE
Joe Ewing is outstanding perfessional.I steffaningly would call again Well done
Nice Tech, Bad pricing
Dipres - Bear, DE
Your company should have communicated better prior to the appointment. I explained the one very simple job to be done and due to your company policies the tech said he needed to offer me all these different longer term service options. He would have been able to change the light switch for $250!!! Are you kidding? No thanks! The service man was very professional and nice, but the price for that job was unreasonable.
Great, informative service!
Walsh - Bear, DE
Clay was very personable. He was very knowledgeable and shared some information about my system and our thermostat functions. Thanks for such a great service call!
Taylor - Bear, DE
Very good efficient friendly
Baliyan - Bear, DE
Campbell - Bear, DE
Teck was very , very good. Knew exactly what the problem was and explained what it was to me . Replaced the thermostat and the unit responded the way it should, problem solved. He ran a test and knew what was wrong. Great guy and I wold like to request him for future work on our unit. Thank you very much DLC
Customer - Bear, DE
Moon provided super quick professional service after we had damage from a tornado. Thank you :)
Esenyan - Bear, DE
Great service as always
Keagy - Bear, DE
Kind - Bear, DE
Fantastic job, courteous and cautious. I appreciate the service that was provided.
Taylor - Bear, DE
Taylor bob - Bear, DE
Very knowledgeable and friendly. Explained all service work in detail
Excellent. Well satisfied.
Donald (Ruth) - Bear, DE
Very good job. Enjoyed talking with the installers
EdA - Bear, DE
Craig was personable and thorough. I feel better knowing our heating system is ready for the winter.
Chin - Bear, DE
Noon services was quick with getting out to my house within a few hours of initial contact. Andy was very polite, informative, and efficient.
Great Service, Always in time
Hogate - Bear, DE
Gamble - Bear, DE
Answered all my concerns Told me everything he was doing very professional
Wonderful service by a personable young man
Lois - Bear, DE
Thank you for your service. Clay did a fine job.
Ottolini - Bear, DE
I would recommend Moon Air to anyone.
Cooling Inspection Indoor unit supply is 65 with a 77 return and 12 delta. Old filter clogged leading to ductwork to sweat, changed filter company supplied due to promo. Voltage enhancement system read 9mfd with a factory setting of 10mfd and has failed. Board and connections are fine. Blower dirty, spins without restriction. Checked heat exchanger for safety. Outdoor unit voltage enhancement system read 5.1/45.8 with a factory setting of 5/45 and is within allowable fault. FLA 0.6 with a factory setting of 1.5 and RLA is 6.1 with a factory setting of 14.1. Coil is very dirty recommend cleaning. Checked disconnect for safety. System normal operation at this time.
Removed old indoor heat transfer media, installed new heat transfer media. Cleaned copper and brazed with nitrogen pressure tested to 400 psi. Held for 30 minutes. Triple evacuated to 140 microns, did decay test for 10 minutes system did not rise above 370 microns. Purged hoses added factory charge adjusted sub cooling to 7-8 operation normal at this time
Warranty from install, gas leak at fitting at furnace, replaced fitting.
No A/C, outdoor pumping system runs but fan does not due to failed voltage enhancement system, factory spec 45/5, actual 40.1/0, installed replacement and test ran, suction 74 psi, outdoor air movement is out of balance, however do not recommend any other repairs due to age and obsolete coolant.
Cooling rejuvenation Indoor unit has a supply of 49 with a return of 70 and a delta of 21. Static pressure supply is 0.5 and return is 0.2. Blower amps were 2.7. Both sides of coil clean, pan clean. UV light working, cleaned air ranger and replaced old media with new. Board and connections fine. Blower fine, spins without restriction. Outdoor unit voltage enhancement system read 5/43.8mfd with a factory setting of 5/45mfd. FLA 1.1 actual 0.6 and RLA 16.7 actual 6.3. Cleaned coil and exterior, interior drain holes clear. Checked disconnect for safety and system normal operation at this time.
A/C / Furnace Rejuvenation Preformed Inspected indoor unit, Inspected electrical components for any burnt or loose connections, blower is clean, cleaned out condensation line with C02 gun and showed customer how to properly use EZ trap, customer is aware filter needs changed Furnace, burners came right inline properly and flame looked good, indoor capacitor still in factory spec, and delta T was 20f. Customer had a concern about possible gas leak, I got whiffs of gas myself, put spray bubbles on all connections. Found possible leak. Customer would like service tech to come out. Ducts are properly installed and secure Inspected outdoor unit. Inspected for any burnt or loose connections, cleaned out electrical cabinet, whipped down unit, coil and inside of unit are clean, capacitor is still running in factory spec. Unit is properly heating/cooling at this point in time
Club ac service. Checked air filter it was recently changed. Temperature is 49 degree, return Temperature is 67, total delta t 18 degrees tested drain with 1 gallon of water and cleaner. Checked evaporator coil it is clean checked eletrical conections on control board. Checked voltage gateway coil is buzzing and does no look good. Checked voltage enhancement system it read 40/9 cs factory spec of 45/10, And is below factory spec. Checked eletrical conections. Brushed out eletrical cabinet. Fla 1.1 rla 8.5. Removed leaves from bottom of condenser and used light cleaner on coil. Operation normal at this time