Moon Air provides fast, reliable air conditioning, heating, and electrical services to the residents of Aberdeen, MD and the surrounding areas!
We pride ourselves on a high standard of customer service. Read our reviews and find out why your neighbors consider us to be their preferred HVAC company and electrican in Aberdeen, MD.
for Aberdeen, MD
Our Reviews by City
Sieranski - Aberdeen, MD
Pulled and cleaned blower wheel and blower assembly. Brushed down evaporator coil and cleaned with cleaner. Wiped down blower motor, wiped down all insulation, poured 1 gallon of water and cleaner down drain line also cleared with co2. Changed capacitor for outdoor unit brushed out eletrical cabinet. Rinsed outdoor coil with water. Replaced contactor, replaced eletrical whip and replaced discounect. And Replaced insulation on Suction line. System running with a 20 degree delta t.
Installed and terminated flexible metal cables for two sump pumps, outside sign and UF cable for split unit. Pull new UF cable for unit in attic. Cable needs to be terminated and a new cable must be installed for basement unit.
Put another MOON stop/warranty sticker on system with date of installation, customer will not be able to change the filter in it's current location, need to go over job with steve moon to see what we can do for them. Best possible solution would be to cut filter rack in on side of furnace and tap the return flex into that and patch the top of furnace. Also recommended they sign up for the gold club.
The new light is mounted above the roof of the front porch. We will need to connect between signs with a piece of 1/2" conduit and another piece of 1/2" condiut from the top sign into the overhanging soffit. A piece of 1/2" conduit will need to come from a security light into the overhang to create a service for the new light. An extension ladder is needed to install conduit from exsiting to overhang. There is a handicap ramp in front of the sign. The roof below new sign is smooth and slippery.
16 SEER 90% Furnace Found too many items on circuit to furnace. There is a dishwasher a disposal and 2 outdoor shed and garage on with the furnace.,
Installing new 16 SEER AC and 96% Furnace with all necessary code upgrades and Harford County Permits.
A/C inspection, all electrical connections are tight, compressor run load amps factory spec 28.6, actual 10.3, outdoor fan full load amps factory spec 1.0, actual .8, voltage enhancement system factory spec 55/7.5, actual 53/7.4, system operation within factory specifications at this time.
1.6 amps blower strip heat 39.3, checked outdoor unit and found to be overcharged, factory spec at 67' indoor and 47' outdoor, suction 104, discharge 335, actual 120/430. In addition the customer told us that his unit was stollen and he had a friend of his recharge it.
16 SEER Heat Pump and air handler
Installing new Amana 16 SEER Heat Pump and Air handler with 10 year parts, 10 year labor, and lifetime unit replacement warranty. Working with Bel Air Lowes and Stephen Plomchok.
No heat, found failed pressure switch, installed replacement, test ran.